The generators are to be used in town , the countryside , work sites , Mountain and pasture lands as a electric power source for lighting purpose , It can also be used as a reserved power Source for emergent case . The generators are of drip – poof with rotary field type and with the adoption of harmonic excitation system . that allow your easy operation and simple maintenance , The generators are of three – phase four – wire type , making use of atar connection with neutral point . The rated line voltage is 400V . Phase voltage 230V . Frequency 50Hz . power factor 0.8 ( lag ) . It can provide 60Hz and the other voltage’s generator according to necessary . They can be coupled with a prime mover directly or through V – belt making right or reverse continuous rotation at the rated speed . when the revolution slip of prime mover is 3 % and load varies in the range of 0 – 1 00 % cosΦ 1.0 – 0.8 they give Food constant voltage. After sudden change ( increase or decrease ) of load . the generators constant voltage . will soon return to their normal working state , without any starting devices the generator can directly start an unloaded squirrel cage lnduction motor.